|Type||RDL302||Dry Sludge(DS) treating capacity||100-140kg/h|
|Solid content||10000-50000mg/L||Output sludge moisture content||75-85%|
According to customer's requirement
|Motor protection level||IP55 F|
|Net weight||1350kg||Operating weight||2000kg|
|Energy consumption of the whole machine|
|Water consumption||80L/h||Water supply pressure||0.1-0.2MPa|
|Flocculant consumption||2-8g-PAM/kg-DS, when the concentration of PAM is 0.1-0.2%|
(PAM means Polyacrylamide)
|Detailed list of pipeline connection|
|Pipe port for sludge inlet||DN65 Flange Connection PN1.0Mpa JB/T81-94|
|Pipe port for filtrate outlet||DN150 Flange Connection PN1.0Mpa JB/T81-94|
|Pipe port for return flow||DN100 Flange Connection PN1.0Mpa JB/T81-94|
|Pipe port for sewage outlet of mixing tank||DN50 Flange Connection PN1.0Mpa JB/T81-94|
|Pipe port for flushing water inlet||DN20 Internal Thread Connection G3/4"|
|Pipe port for polymer inlet||DN25 External Thread Connection G1"|
|Electric control panel||SS304/SS316|
1. The electronic control system can be customized according to customers'requirements.
It can add PLC and communication module.
|2. For detailed information and drawings, please contact our engineer.|
Dewatering Screw Auger Press which uses the screw extrusion principle is a new type of solid-liquid separation device.
It reaches the goal of extrusion dewatering sludge by the powerful extrusion pressure of changing the screw diameter and distance, and the tiny spacing between moveable annular plates and fixed annular plates.
Sludge will be transported to the dewatering department after being thickened in the thickening department.
In the advancing process, great pressure has been produced because of the gradually decreasing filter spacing and screw distance, and the back platen clogging.
Then the volume decreases continously, and the purpose of fully dewatering will be achieved.
The main body of the Dewatering Screw Auger Press is made of multiple fixed annular plates and moveable annular paltes with the screw shaft running through it.
The front part is thickening department and the ending part is dewatering department.
It can thicken and dewater sludge in one box, and has taken place of traditional filter clothes and centrifugal filtration method for its distinctive filter model.